||Plans approved by the Fire Marshal give authorization for construction. Final approvals are subject to field inspection and verification. Any approval issued by the Fire Marshal does not release the contractor or property owner from responsibility of full compliance with all applicable codes and ordinances relating to the construction project. All installations must concur with approved plans. Any deviation from the approved plans requires a re-submittal to the Fire Marshal’s Office, PRIOR TO INSPECTION. Failure to submit revised plans prior to the inspection may result in a delay for inspection and sign-off.|
Plans must be submitted to Development Services located at 200 Sidney Baker St. North, Kerrville, TX.
A copy of 5 sets of plans must be submitted along with a PDF copy of all material submitted.
All plan submittals must be accompanied by a Fire Protection Plan Review/Permit Application. NO EXCEPTIONS.
All plan submittals must be accompanied by a copy of their respective Texas State Fire Marshal’s Office License (TSFMO) and Liability Insurance with the City of Kerrville listed as the certificate holder.
All plan submittals and calculations must be signed by a TSFMO Licensed Contractor, Qualified Fire Protection Engineer or a Qualified Professional Engineer.
Payment will not be accepted until a final approval of plans.
Plan Review Time and Hierarchy
It is the goal of the Fire Marshal’s Office to complete your plan review within the shortest possible time. We strive to complete your plan review within ten (10) business days from receipt of complete plan submittal package. Please be advised that revisions, changes or an incomplete submittal package may delay your final plan approval.
Plans are reviewed based upon the hierarchy of fire protection systems. That is, the fire sprinkler overhead will not be reviewed until the fire sprinkler underground has been permitted and the fire alarm will not be reviewed until the fire sprinkler system has been permitted.
This same rule is applied to civil and building construction plans. Civil plans are not reviewed until the Site Plan is approved and building construction plans are not reviewed until the civil plans have been approved.
Plan Submittal Guidelines
These guidelines are to be followed when a submittal for a permit is required by the Kerrville Fire Marshal for installation, modification or otherwise required within the City of Kerrville.
All requirements for the purposes of these guidelines shall conform to the International Fire Code 2006, as adopted and amended by the City of Kerrville and any applicable NFPA standards.
These guidelines do not replace or supersede any codes and/or ordinances adopted by the City of Kerrville, or determinations and positions of the Fire Chief or Fire Marshal.
To open the following documents you will need the latest version of Adobe Reader.
Fire Permit Application
Amendment to the 2006 Edition, International Fire Code
Open Burning in Texas